Payment & Shipping Terms:
|Type::||T - Type||Impact Force:||Powerful|
|Sample:||Free 10 Pcs||Short Circuit Strength:||120A / Mm|
T - type connector terminal Block Connector Waterproof Voltage 1000V
JXT2 series T-type connector is used for branch line “T”connection in the construction and industrial electric equipment when cable trunk can't be cut off. On the basis of advantage of TJXT1 series T-type connector, it shows its highlight of safety protection, and makes a breakthrough in design. This launch of the connector, not only greatly increases the performance/price ratio, but also expands the service range, so as to provide designer with enough imagination space. It stands out in the industry of cable T-type connector. The products are in conformity with IEC60947-7-1,GB1404B.7,1 and JB/9659.1.
1.Easy branching of trunk line when the cable is not cut off, flexible combination.
2.Reliable connection of copper or aluminum conductor and the transition between copper and aluminum
3.All electric performance parameter in accordance with IEC requirements, perfect electricity conductivity, low resistance loss, little voltage drop, and the contact drop1.98V.
4.Strong heat endurance and impact resistance, withstanding short-circuit strength test of 120A/mm2, the insulator foot made of incombustible material of VO class, shows perfection in aging resistance.
5.Convenient installation, saving time for construction, not need lug, realizing bare conductor connection, favored by construction teams.
6.Compared with plug-in bus ducts and branch cables, it can save 50%~70% of engineering expense.
This series of connector is composed of insulator foot, wire frame, protective cover. The wire frame is made up of clamp, screw, nut and supporting fixture, etc.A closed interlocking structure is formed between clamp and conductor contact surface with large ,contact surface and reliable crimping, Through combinations of different shapes of clamps, a double-layer connection can be formed, which makes the trunk line be connected from the lower layer and branch line be connected from the upper layer. Thus,“T”connection is formed. The product is protection type, especially suitable for the narrow locations like cable tray and cable shaft, to effectively prevent the circuit being damaged by mouse.
Three ways to install this series of connector:
1.Plug it in the mounting rail (TH-35 top-hat rail),(only for type JXT1-50).
2.Attach it to the trunk line after connection.
3.Mount it on the bottom plate or wall with the screw, adopt the way of diagonal line installation with two mounting holes
Instruction for use:
① Open the protective cover
② Take the screw and clamp out, connect the trunk line and assemble the clamp and screw
③ Put the protective cover on and tighten the mounting screw
④ Open the top transparent cover, loosen the connection screw, then connect the branch wire, at last tighten the screw and shut the transparent cover down.
|Model No.||Voltage/Current||Cable Size (mm2 )||Bolt||Torque Nm||Length of skin to be removed|
|JXT2 50(35)||1000V/ 150A||Main10∼50,branch6∼35||M8||12||25/25|
|JXT2 70(50)||1000V/ 192A||Main25∼70,branch10∼50||M10||20||30/30|
|JXT2 95(70)||1000V/ 232A||Main25∼95,branch10∼70||M10||20||30/30|
|JXT2 95(70)B||Main 25∼95,branch2*10∼35|
|JXT2 185(150)||1000V/ 353A||Main35∼185,branch10∼150||2×M10||20||50/50|
|JXT2-240(95)||1000V/415A||Main 35∼240,branch 10∼95||2×M10||20||50/50|
Contact Person: Jason